Short Circuit Current Ratings
Marking equipment and industrial control panels with their SCCR is required by UL 508A
Additionally, the NEC requires industrial control panels be marked with the assembly SCCR as well (409.110, 670.3(A), 440.4(B). Together, the NEC and OSHA require that electrical equipment provide sufficient protection against short-circuit current events. 1910.303(b)(5) of the OSHA regulation requires all electrical equipment meet this requirement.
Eaton makes compliance easy with three great resources
1. SCCR Protection Suite
Eaton’s SCCR Protection Suite is a comprehensive product portfolio that provides equipment designers easy access to a wide selection of circuit protection and wiring distribution/termination to switching devices to meet a broad range of SCCRs needs from 18kA to 200kA. These solutions help designers eliminate weak links by identifying solutions that raise the component SCCR or limit the fault.
2. OSCAR SCCR Compliance Application
The Bussmann OSCAR SCCR Compliance Application easily guides subscribers through entering an electrical panel’s components and calculates the equipment’s SCCR, and provides one-line diagrams and detailed documentation for the determined SCCR level. This award winning, online tool provides a quick and accurate means for compliance with 2014 NEC and UL 508A Supplement SB equipment SCCR marking requirements.
3. FC2 Fault current calculator Mobile App
Knowing available fault current levels is vital for compliance with SCCR requirements in NEC and OSHA. Bussmann’s FC2 Calculator mobile and web-based application is a free tool that provides an easy means for calculating fault current levels and generating NEC 110.24 compliant labels and one-line diagrams. The mobile version is available for Apple and Android devices.
Understanding and planning for SCCR
Both industrial equipment manufacturers and users need to know about SCCR, and the related code and regulatory requirements. The following documents will help you gain insight into this often misunderstood subject and how you can effectively plan and implement an effective SCCR strategy.
- Application Note No. 10367 - Developing an effective SCCR plan for facilities and purchasers of industrial equipment
- Application Note No. 10368 - Developing an equipment SCCR standard for manufacturers of industrial equipment
- Brochure No. 10374 – Equipment SCCR made easy
- Whitepaper No. WP083020EN – Applying current-limiting devices to raise SCCR
- Listicle - 10 products and tools that help raise panel SCCR