BR plug-on neutral (PON) circuit breakers
Please follow these specific steps when installing Eaton’s BR PON circuit breakers.
Please note: Install long-body BR breakers (2 pole GFCI, 2 pole AFCI, or surge) towards the bottom of the BR plug-on neutral loadcenters below the twin neutral bars.
CH plug-on neutral (PON) circuit breaker
Please note: As stated on all CH PON loadcenter interior labels (figure 3), the neutral bar screws are not to be backed out, and the wire is not to be installed in the neutral bar terminals beneath the CH PON breakers. Failure to follow this specific instruction may prevent proper installation.